Chapter 16. Plumbing
Sec. 16-21. Water service materials and depth.
(1) All water pipes or lines laid underground shall be of type K copper tubing polywrapped, Class 52, cement lined, ductile iron from the city water main to the curb stop. After the curb stop, other material may be used as provided at SPS 384.30.
(2) All water laterals from the city water main to the lot line shall be laid in accordance with the provisions of section 16-24(3), (4) and (5) of this chapter.
(Code 1982, § 15.07; Ord. No. 998, § 3, 10-27-2003)
Back to Chapter Table of Contents